Advanced Cooling Technologies, Inc. has developed an Applied Nanoscale Corrosion Erosion Resistant (ANCERTM) coating to protect the heat transfer surfaces in copper heat exchangers used with De-Ionized Water (DIW) as the coolant. The coating, applied by vapor deposition techniques, is both inert (to protect from corrosion) and hard (to protect from erosion). The ANCERTM coating is applied at nanometer thickness and therefore does not hinder the thermal or hydraulic performance of copper heat exchangers, even as flow channels approach the micro-scale. Additionally the coating provides corrosion protection in DIW coolant with a wide range of pH and Dissolved Oxygen (DO), thereby reducing the strict water quality control requirements for DIW systems.
Copper heat exchangers utilizing high velocity, high purity, de-ionized water (DIW) coolants undergo degradation from erosion-corrosion, also known as flow assisted corrosion. Under this degradation mechanism, the passive, native oxide layer of copper is removed by the erosion forces of the high velocity DIW, thereby exposing the active, underlying copper substrate, as shown in Figure 1.
The native oxide layer protects the copper from corrosion damage, thus removing the passive layer makes the underlying copper more susceptible to corrosion damage. Over time, the erosion-corrosion mechanism degrades heat transfer surfaces and consequently hinders the thermal performance of the heat exchanger until it ultimately needs replacing. The current method to extend the lifetime of copper heat exchangers in DIW cooling systems is to apply a nickel and gold plating on the internal features of the heat exchanger or control the DIW properties in a tight pH and dissolved oxygen (DO) operating range. However, as heat transfer surfaces approach the micro-scale, nickel and gold plating techniques can no longer provide uniformity presenting either pin-holes or clogging of the micro-scale flow passages, as shown in Figure 2.
Furthermore, controlling the DIW properties requires costly monitoring and control hardware to maintain the DIW coolant within the desired operating range, and unforeseen failures can occur in the event that these systems fail. To evaluate the level of passivation provided to copper heat exchangers in DIW systems, ACT conducted corrosion evaluations using electrochemical techniques to evaluate the corrosion rate of uncoated and ANCERTM coated copper in 0.3 MΩ·cm DIW in pH ranging from 6 to 9 and DO ranging from 0.5 to 10 ppm. The results are shown in the copper release maps (contour plots of corrosion rate against pH and DO) below; see Figure 3.
The copper release maps in Figure 3 demonstrate that the ANCERTM coating provides a one to two order of magnitude reduction in corrosion rate compared to the baseline copper sample. Additionally, the copper release maps exhibit the dependence of the corrosion rate of the baseline copper sample on the DIW coolant conditions and the consistent corrosion rate of the ANCERTM coated sample across a wide range of pH and DO. Thus, the ANCERTM coating provides corrosion protection across a wide range of DIW coolant pH and DO and reduces DIW control requirements and provides protection in the event of failure of DIW coolant conditions systems.
The erosion-corrosion protection in extended exposure to high purity DIW was evaluated by measuring the corrosion rate using electrochemical techniques at predetermined time points throughout a 1,000 hour exposure to 0.3 MΩ·cm, pH 6, DIW with a linear velocity of 3.8 and 4.8 m/s for bare copper, nickel and gold plated, and ANCERTM coated copper samples.
As shown in Figure 4, the corrosion rate of the ANCERTM coated copper sample exhibited the lowest corrosion rate. Furthermore, this corrosion rate was consistent throughout the 1,000 hour duration and between the 3.8 and 4.8 m/s linear velocities, thus indicating protection from erosion. However, the nickel and gold plated sample exhibited an increase in corrosion rate throughout the duration of the 1,000 hour test and exhibited a larger increase in corrosion rate at higher flow rates indicating damage from erosion. Thus, the ANCERTM coating exhibited long term protection in erosion and corrosion.
The thermal and hydraulic performance of copper heat exchangers used in laser diode thermal management was evaluated by measuring the pressure loss and thermal resistance of ANCERTM coated and uncoated copper heat exchangers. As shown in the plots below, the pressure loss and thermal resistance of ANCERTM coated and uncoated heat exchangers were equivalent demonstrating that the coating does not impeded the thermal or hydraulic performance of the heat exchanger.
The ANCERTM coated and uncoated copper heat exchangers used in laser diode thermal management were evaluated for 200 hours in high velocity, 0.3 MΩ·cm, pH 6 DIW and the pressure coefficient of the respective coolers was monitored throughout the duration of the test, as shown in Figure 6.
The deviation in pressure coefficient from 1 indicates a change in the hydraulic diameter of the flow channels within the heat exchanger. As shown in the figure above, the ANCERTM coated samples exhibited a pressure coefficient stabilized at 1 throughout the duration of the 200 hour test, demonstrating protection from erosion/corrosion degradation, whereas the uncoated bare copper heat exchangers exhibited deviations in pressure coefficient that indicate a change in hydraulic diameter of the heat exchanger, and no protection. For a detailed description of test conditions and results of the ANCERTM coating in copper heat exchangers for laser diode thermal management, see ACT’s manuscript entitled A Corrosion and Erosion Protection Coating for Complex Microchannel Coolers used in High Power Laser Diodes presented at ITherm 2014.
- Advanced Coatings
- Applied Nanoscale Corrosion Erosion Resistant (ANCER™) Coatings
- Boiling Enhancement/Micro-porous Coatings
- SAM Coatings for Condensation Enhancement
- Plasma-Enhanced Chemical Vapor Deposition (PECVD) Coatings